STEAM LINE CONDITIONING CONTRIBUTION
“STEAM LINE CONDITIONING CONTRIBUTION”
It is a mixed product consisting of volatile-neutralizing-film-making and corrosive gas absorbent amines and amintures in an all-organic structure.
Low and medium pressure (max.45 ) is used to prevent corrosion in steam circuits and to achieve the desired quality of condensate water.
The carbon dioxide formed in the steam boiler turns into carbonic acid in the condensate lines and causes corrosion. CND 6100 reacts with CO2 to neutralize carbonic acid. Since this structure adapts to all phases of water and steam, CND 310 circulates through the entire system as amine carbonate. Meanwhile, they prevent the formation of corrosion by binding oxygen to other active substances in CND 6100 Decongestant. In addition, by increasing the pH value of condensate water (8-9), the corrosion caused by pure water is stopped.
- pH 12.00±0.5
- 1% Ph 11.00±0.2
- Density (25°C) 0.990
- The Resolution Is Infinite
- Appearance Colorless, clear, liquid
According to the boiler fattening water and operating characteristics, it will be determined according to the analyses performed by the company control engineers.
Original Thumblock cover 30 – 60 – 200 kg is shaped like a canister. It maintains its stability for a period of one year in its packaging, above freezing point temperature and in closed warehouse conditions.